Dana Keypad109 Views •
Smoke Detector96 Views •
IQ Panel 2 Plus93 Views •
Wireless Door/Window Contact89 Views •
Doorbell Chime88 Views •
Video Doorbell88 Views •
Relay Module87 Views •
Occupancy Sensor80 Views •
Outdoor Bullet Camera79 Views •
Inline Switch/Dimmer79 Views •
Guardian Camera78 Views •
Main Repeater77 Views •
PIR Motion Sensor77 Views •
Danalock76 Views •
Indoor Dome Camera76 Views •
Inline Dimmer73 Views •
Lighting Keypad72 Views •
Sonos One69 Views •
Sonos Five69 Views •
Sonos Roam68 Views •
The PowerG Wireless Smoke and Heat Detector alerts you to early warning of fire.
It alerts the room's occupants by activating the built-in alarm. When smoke or temperatures above 57°C have been detected, an alarm buzzer and a flashing LED light are activated.
Simultaneously, it sends a coded signal to the control panel to sound the system siren, alerting the end user and/or central control a monitoring station to dispatch on-site assistance.
Battery Life: 3 years (typical use)
Battery Type: 3 AAA batteries (included)
4.8mm Phillips screwdriver
Screw Gun (for mounting with screws)
UNBOXING THE SMOKE DETECTOR
Inside the package, you should find
Battery: 3 AAA batteries
PowerG Smoke Detector
NB - DO NOT locate smoke detectors at the top of peaked or gabled ceilings (at the top of double volumes. Generally, avoid areas with turbulent air flow, such as near doors, fans or windows.
DO NOT locate detectors in areas of high humidity.
MOUNTING THE SMOKE DETECTOR
Ideally, the Smoke Detector is mounted at the center of the room. Also, ensure that the detector is in line with other ceiling fittings (e.g. lights, access points, etc).
Mount the detector backplate. Install the mounting base on the ceiling using screw locations as required. Use the two screws, anchors provided and a screw gun to screw into hard walls.
Fit the detector inside the base by aligning it over the base. The detector's alignment notch
should be slightly offset from the mounting base tamper release tab. Then turn the detector
clockwise until it clicks into place.
Remove the detector from its mounting base by twisting the detector counterclockwise.
Carefully remove batteries by lifting from the “+” end using a flathead screwdriver and dis-
pose of them according to local regulations.
To ensure a proper power-down sequence, wait a minimum of 30 seconds before
installing new batteries.
Install 3 new AAA batteries, available from a local ‘Duracell’ or ‘Energizer’ dealer in the battery compartment. Install the batteries by inserting the “-” end first, then pushing the “+”
If the batteries are incorrectly inserted, remove them carefully by lifting them out from the “+” end and correctly re-inserting them
Re-install the detector on its mounting base by turning the detector clockwise until the mating marks align.
After the power-up sequence, the green LED should blink once every 60 seconds to indicate normal operation.
To install this Web App in your iPhone/iPad press and then Add to Home Screen.